The Clare Controls CLIQ.host controller provides all device management services to AppModules, supports all Clare user interface services, and acts as the gateway to the ClareCloud for system updates. The controller comes complete with the ClareOS and all AppModules preloaded. The controller also comes equipped with a 908.4 MHz transceiver for controlling your other devices, such as integrated lighting, thermostats, sensors, and door locks.
Note: Models are subject to change without any prior notice.
WARNING: Any changes or modifications made to this product not expressly authorized by the manufacturer could void the user’s right to operate this device.
Remove all contents from the CLIQ.host packaging and ensure you have the following items.
Record the device’s UUID number (labeled on the bottom of the device) on the line below, or scan the QR code (also on the label) with a scanning app, and then email the number to your system programmer. Your system programmer will need this UUID information to configure the CLIQ.host device.
Do not use this UUID for more than one account.
WARNING: Do not apply power to the CLIQ.host until installation is complete. Failure to do so may result in bodily injury and/or damage to the equipment.
Note: The CLIQ.host contains a 908.4 MHz transceiver. To prevent radio frequency (RF) interference from external sources, we recommend that you place the CLIQ.host away from devices that may cause interference and away from conductive metals.
When mounting the CLIQ.host in a structured enclosure, we recommend using the Leviton Structured Media Enclosure or the Suttle SOHO Access Enclosure panels fitted with the ClareHome Structured Enclosure Extender (P/N CH-EXT-28 and CH-EXT-42) for added protection against heat build-up. (Panels and extenders are sold separately.)
1. Place the CLIQ.host inside the structured enclosure with the rear of the device facing up, see Figure 1.
2. Using cable ties, secure the CLIQ.host to the enclosure.
Note: Be sure to leave at least 1U of spacing (1.75 in. (4.45 cm)) above and below the CLIQ.host when mounting.
After placing your CLIQ.host, make the connections to your other devices. Figures 2 and 3 identify the LEDs and ports on the front and rear of the CLIQ.host. Refer to the documentation that came with each of your other devices for detailed information about connecting those devices to the CLIQ.host.
1. Connect your serial devices (optional) to either of the two RS-232 ports using an RJ12 to RS-232 cable, or an RJ12 to DB9 null modem cable (included). See Figure 3, item 1. For RJ12 pinouts, see Figure 6.
2. Connect your IR devices (optional) to the 12-pin terminal connector (included), and then insert the connector into the port labeled “IR Outputs.” See Figure 3, item 2.
If your IR device comes with a 3.5 mm connector, you will need to cut and strip the wires before connecting it to the terminal connector.
When connecting an IR emitter, attach the striped wire to positive (+) and the black wire to negative (-).
3. Connect a CS-BR-1 Streams Audio Bridge (optional) to a USB port on the CLIQ.host. See Figure 3, item 3.
Note: The USB connection allows the CS-BR-1 to encode up to three simultaneous audio streams onto the CobraNet network.
4. Connect your digital I/O devices (optional) to the 8-pin terminal connector, and then insert the terminal connector into the port labeled “I/O.” See Figure 3, item 4.
When connecting devices, wire it such that ports 1 and 2 share the same 12 VDC power and ground and ports 3 and 4 share the same power and ground.
5. Use an Ethernet cable (not included) to connect your CobraNet switch to the port labeled “CobraNet.” See Figure 3, item 5.
Note: The CobraNet port is preset with the static IP address 172.30.100.1. All CobraNet devices used on the same subnet must use an address from 172.30.100.2 to 172.30.100.254.
6. Use an Ethernet cable (not included) to connect to your data network switch to the port labeled “Ethernet.” See Figure 3, item 6.
7. Connect relay contacts (e.g., garage door contacts) to the 6-pin terminal connector, and then insert the terminal connector into the port labeled “Relay.” See Figure 3,
8. Attach the 908.4 MHz antenna or optional antenna extender to the antenna port. See “Attaching the antenna” below.
The 908.4 MHz antenna can be mounted to the CLIQ.host controller, or further away using an extender cable (included) to enhance radio performance. When mounting the CLIQ.host inside a structured enclosure, always mount the antenna outside the enclosure using the extender cable.
1. Remove the 908.4 MHz antenna from its packaging.
2. Screw antenna to the antenna port on the rear of the CLIQ.host until the antenna is snug. Do not over-tighten the antenna. See Figure 4.
1. Using a 17/64 in. drill bit, drill a hole in the sidewall of the ClareHome Structured Enclosure Extender, near the CLIQ.host.
2. On the extender cable, remove the locknut and washer from the SMA Male connector. See Figure 5.
3. Insert the threaded end of the connector though the hole, and then replace the washer and locknut, tightening the locknut until the connector is secure and does not wobble in the hole.
4. Screw the antenna to the connector until the antenna is snug.
5. Attach the other end of the extender cable to the antenna port on the rear of the CLIQ.host. See Figure 3, item 8.
If you are using your own RJ12 cable (rather than the one supplied), ensure your RJ12 cable connector pinouts match the pinouts on the RS-232 ports, as shown in Figure 6.
Plugging in the power adapter automatically turns on the CLIQ.host and starts the boot process.
1. Plug one end of the power adapter into a power receptacle on the back of the CLIQ.host labeled “12vdc.” See Figure 3, item 9.
2. Check the LED on the front of the CLIQ.host. It illuminates purple when booting and blue when running normally. See Figure 2, item 1.
Your CLIQ.host controller automatically detects and sets its time, date, and time zone when you connect it to your data network. CLIQ.host uses NTP and synchronizes the date and time at boot up and periodically throughout the day.
Refer to the Fusion Configuration Tool Administrator Guide (Doc ID 069) for instructions on creating, testing, and deploying a project. When you deploy the project from Fusion, it will deploy to the CLIQ.host.
To prevent the unit from sliding, use the four rubber foot covers included with your CLIQ.host.
Clare Controls offers a three (3) year limited warranty on original Clare Controls components, from the date of shipment from Clare Controls. To view complete limited warranty details, including limitations and exclusions, www.clarecontrols.com/warranty.